§ 109.1106. Design standards.
Corrosion control treatment facilities shall be designed to satisfy the following standards unless the Department determines that the requirement is not technologically feasible or is not necessary to optimize corrosion control:
(1) A minimum pH measured in distribution samples of at least 7.0.
(2) For systems that are exempt under § 109.1105(b)(1) or (2) (relating to permit requirements) from submitting a construction permit application, a minimum alkalinity measured in all distribution samples of 20 mg/l.
No part of the information on this site may be reproduced for profit or sold for profit.
This material has been drawn directly from the official Pennsylvania Code full text database. Due to the limitations of HTML or differences in display capabilities of different browsers, this version may differ slightly from the official printed version.