§ 2800.131. Fire extinguishers.
(a) There shall be at least one operable fire extinguisher with a minimum 2-A rating for each floor, including public walkways and common living areas every 3,000 square feet, the basement and attic.
(b) If the indoor floor area on a floor including the basement or attic is more than 3,000 square feet, there shall be an additional fire extinguisher with a minimum 2-A rating for each additional 3,000 square feet of indoor floor space.
(c) A fire extinguisher with a minimum 2A-10BC rating shall be located in each kitchen of the residence. The kitchen extinguisher must meet the requirements for one floor as required in subsection (a).
(d) Fire extinguishers must be listed by Underwriters Laboratories or approved by Factory Mutual Systems.
(e) Fire extinguishers shall be accessible to staff persons. Fire extinguishers shall be kept locked if access to the extinguisher by a resident could cause a safety risk to the resident. If fire extinguishers are kept locked, each staff person shall be able to immediately unlock the fire extinguisher in the event of a fire emergency.
(f) Fire extinguishers shall be inspected and approved annually by a fire safety expert. The date of the inspection shall be on the extinguisher.
No part of the information on this site may be reproduced for profit or sold for profit.
This material has been drawn directly from the official Pennsylvania Code full text database. Due to the limitations of HTML or differences in display capabilities of different browsers, this version may differ slightly from the official printed version.